There are various types of filters available in a V-bank or flat panel configuration There is a wide range of filters available from low grade cleanable filters all the way up to high efficiency cartridge or bag type filters Some applications require a combination of different efficiencies.
When choosing higher efficiency filters, one should seriously consider the use of a backward incline or airfoil fan in place of the standard forward curve fan These specialty fans are recommended so the customer is able to get full use of the filter capacity while maintaining the same CFM level of air delivered. Forward curve fans will experience reduced performance when high efficiency filters load up. Reduced airflow could adversely affect a customer’s operation or process.
It is important for the installer to adequately support all filter sections that are shipped as loose items.
Cleanable filters are generally used in industrial applications where the filtering of large, coarse particles is required. While they are not as effective at removing particles from the air as other filter types, they do have the added benefit of being resuable as the buildup can be removed by cleaning.
EZ Kleen Air Filters -
Cleanable Aluminum Filters
Disposable filters are more effective than cleanable filters in terms of removing particles from the air. However, they must be replaced once clogged by the particles that are filtered from the air. Titan offers a variety of filter types included pleated, linked panel, rigid, and bag filters.
Camfil: Aeroplete III -
Camfil: 30/30 III -
Clarcor Air Filtration -
Camfil: Durafil ES2 -
MERV 11, 13, 14, 16
Camfil: Opti-pac -
Camfil: Hi-Flo ES -
MERV 11, 13, 14, 15
Camfil: XH Absolute -
High capacity HEPA/ULPA grade filter in an all metal 16-gauge enclosing frame
Download PDF Specifications.
Filter Section Photo Gallery
The below gallery shows a variety of different filter section accessories. These accessories are shown only for illustrative purposes, an air handler will have accessories sized specifically for the airflow of the unit.